Courtesy of our magazine readers, check out the latest Caught on Camera Exclusives. Keep them coming…
Andy Craig: “I was called in to connect a heat pump onto a system which was at first fix stage and found this at both ends of the mains! Nice use of twin+earth with SWA to parallel the supply cable through the ground, why bother with glands?”
Inspector says: “This cowboy left his banjos at home.”
Regulation referral: 4126.96.36.199 Earthing of exposed-conductive-parts.
John Geddes: “This was feeding an outside shed. If you look closely the conductors are starting to melt. No RCD protection for the shed either.”
Inspector says: “Should have used 6mm.”
Regulation referral: 533.1 Devices for Protection against overcurrent.