Check out our latest round-up of #CaughtOnCamera shockers! Have you seen something shocking, funny or surprising while on the job? Take a pic and send it in via DM on one of our social channels or send it directly to email@example.com for the chance to be featured!
We’re back with another #caughtoncamera ! This one was sent in by Alan Frewin “Where do you start with this? 3 x 2.5mm supply to DB, piggy-backed from the supply side of the DB above. 2 x 2.5mm singles for earth, bypassed the RCD and mcb. My finger tip (top left corner) is on the load cable to a single socket below – 32A ‘protection’ I suppose is immaterial. Protection will be from the 100A primary fuses at the head. Found in a nursery, reception classroom!”