Check out our latest round-up of #CaughtOnCamera shockers! Have you seen something shocking, funny or surprising while on the job? Take a pic and send it in via DM on one of our social channels or send it directly to firstname.lastname@example.org for the chance to be featured!
Check out this shocking #caughtoncamera sent over by Kevin Smith “This CU change could not have been carried out by an electrician! Undersized cables for OCPDs i.e. 2.5mm off a 32A feeding 5+ kW accumulated loads and 6mm T&E mains tails off a 100A DNO fuse. No grommets, no fire rating, no circuit identification. Conductors not securely terminated. Unsheathed single insulated cables outside of enclosure. Dual RCDs that don’t operate before the upstream 63A 30mA covering whole installation. No main bonding, multiple metallic water pipes entering from the ground. Earthing conductor to electrode poor connection.”
A scary #caughtoncamera we received recently from Terry Homer – “Wouldn’t life be so much easier if we could just do this!”