Darren Bakewell, Applications Engineer at Seaward, provides guidance for electrical inspection and testing of solar PV installations to ensure system safety and performance.
The safe operation of solar PV installations under both normal and fault conditions is an essential consideration at the system design stage to ensure that proper energy outputs and safety levels are achieved. And once in operation, it is important to ensure that the long-term performance of the system is not compromised by sub-standard installation or poor maintenance.
In this respect, there are some key solar PV system features that rely on adequate and appropriate electrical testing and inspection being undertaken on a regular basis.
Compliance with IEC 62446 and BS7671
IEC 62446 recommends that periodic verification of an existing installation shall be performed. The standard defines the minimum requirements for system documentation, commissioning tests and inspection for PV systems. Where appropriate, the results and recommendations of previous periodic verifications shall be taken into account. A report on the condition of the installation shall be provided.
We must maintain our solar PV installations in a safe condition. BS7671 covers electrical design, installation and testing of electrical installations and includes a section on solar PV that may need to be considered differently to other installations. This section makes note of BS EN 62446 for the inspection and testing of the systems.
PV systems, in particular large-scale systems, have many metres of cabling, much of which is buried underground. Poor levels of insulation will allow energy generated by the PV system to leak to earth. This can be particularly problematic during damp or wet conditions where the insulation monitoring or residual current monitoring function within an inverter prevents the inverter from starting up which in turn can significantly reduce the operational efficiency of the PV installation.
PV systems by their very nature are exposed to the elements. Damage or corrosion to cabling and connectors caused by moisture ingress can result in degradation in performance or increased risk of fire. Regular inspections and electrical testing will enable system performance to be monitored and any necessary repairs or remedial actions to be taken.
Surface contamination and physical damage
PV modules can become dirty or contaminated over time and this can reduce the operational efficiency and system performance. Similarly, exposure to the elements can result in physical damage to the component parts of a PV installation. Objects dropped by birds can result in physical damage to PV modules which may result in reduced output performance. Periodic inspection and electrical testing as part of regular maintenance will enable any problems to be identified and diagnosed.
Damage to wiring
The most obvious example of bad wiring is when wires hang below the panels and touch the roof or underlying vegetation. Eventually the wire coating will wear or be damaged by rodents and potentially expose the copper wires, presenting a shock and fire hazard. Any deterioration of cable connections and wiring can be identified by applying regular electrical testing to identify potential faults.
Verification of system performance
The verification of system performance and energy output from the panels is particularly important. In many cases simple electrical faults or wiring failures can cause a serious inefficiency in the ability of the system to produce power. Although proper metering will give an indication of system performance, periodic electrical inspection and testing is vital to verify ongoing functional performance over extended periods.
Periodic electrical inspection and testing of solar PV systems to identify and confirm continued safe operation and maximum energy output performance can be required as part of product warranties and PV system component guarantees.
Avoiding fire risks
As the number of rooftop solar installation systems have grown over the years, so have the number of reported incidents of fires. Household fires started by electrical faults in rooftop solar PV systems have been reported in a number of countries, so the periodic inspection and testing of the electrical wiring and components associated with solar PV systems will ensure the safe operation of the system and reduce the potential fire risk associated with any electrical faults.
All solar PV installations require the provision of various documentation and forms to the customer. System documentation usually includes system data, installer details, electrical diagrams, operation and maintenance instructions and other information that may be required by certain standards or regulatory bodies.
Copies of all test and commissioning data should also be provided and as a minimum this should include the results from the electrical safety and verification tests undertaken as part of the system installation procedures.
To browse Seaward’s range of solar PV testing equipment, click here